Is it Sufficient to Use NFPA 70E Tables in Place of an Arc Flash Hazard Study?
Under all circumstances, it is necessary to protect the working personal from dangers associated with live electricity installations. For this reason and to ensure compliance with the OSHA regulations, Arc flash hazard and electric shock hazards need to be evaluated and studied for every facility having an electrical installation.
We just launched our Power Systems Engineering Vlog series and in this series, we are going to talk about all sorts of various power system engineering studies and commentary. We will overview the different blogs written by AllumiaX. It’s fun, it’s lively, it’s a video blog essentially and we hope that you’ll join us and benefit from it.
What is an Arc Flash Hazard, and Why does it Occur?
Arc Flash hazard is the danger of excessive heat exposure and serious burn injury due to arching faults in electrical power systems .
Electric arcs produce intense heat, sound blast and pressure waves. They have extremely high temperatures, radiate intense heat, can ignite cloths and cause severe burns that can be fatal. These arc flashovers occur due to dust on the conductor surface, condensation of vapor, corrosion of equipment parts and even accidental contact with live conductors.
What are the NFPA 70E Tables?
The 2012 NFPA 70E Article 130 tables specify:
· The safe distances or the arc flash boundaries that are to be followed when working on systems that have a voltage greater than 50 Volts.
· The personal protective equipment or PPEs that must be worn when working on systems that have a voltage greater than 50 Volts.
When the NFPA 70E Tables or the Arc Flash Hazard Study is Required?
Whenever any maintenance related or otherwise work has to be done on or near a live electrical installation that may not be brought into a safe working state for a number reasons, two things must be determined to ensure safety of employees.
The NFPA 70E Table Method
Limitations of the NFPA 70E Table Method
Testing NFPA 70E tables is usually the easiest, fastest and most straight forward method to enforce electrical safety standards, however there are some limitations to it.
IEEE 1584 Method for Arc Flash Hazard Analysis
The IEEE 1584 method of arc flash hazard analysis dictates that an arc flash study must be done in association with or follows in continuation of a short circuit analysis study and then a relay coordination study as discussed here comprehensively.
Benefits of Performing an Arc Flash Hazard Analysis
An arc flash study by way of IEEE 1584 method and associated calculations, if done in place of using NFPA 70E tables will bring several benefits for the facility.
Let us know if you have any queries regarding this topic and do provide us with your feedback in the comments.
AllumiaX, LLC is one of the leading providers of Power System Studies in the northwest. Our matchless services and expertise focus on providing adequate analysis on Arc Flash, Transient Stability, Load Flow, Snubber Circuit, Short Circuit, Coordination, Ground Grid, and Power Quality.
About The Author
Abdur Rehman is a professional electrical engineer with more than eight years of experience working with equipment from 208V to 115kV in both the Utility and Industrial & Commercial space. He has a particular focus on Power Systems Protection & Engineering Studies.
Abdur Rehman is the CEO and co-founder of allumiax.com and creator of GeneralPAC by AllumiaX. He has been actively involved in various roles in the IEEE Seattle Section, IEEE PES Seattle, IEEE Region 6, and IEEE MGA.